Much like another of our major internal organs, the oil pan functions in a similar fashion to the liver. It is the prime filter of impurities in our system. Whatever combustion impurities exist inside the walls of the engine, none will avoid detection in the oil pan. An inspection of the oil during a routine change will inform the maintenance technician whether that combustion is complete or suffering from serious problems.
A diesel engine is designed to keep the different internal functions separated from one another: Combustion from lubrication and cooling. Metal rings adorn the perimeter of the piston head to prevent oil and diesel from mixing. Diesel fuel that escapes combustion will stick to the shaft and eventually migrate south into the oil pan. So will another common impurity prevalent in diesel: water. It too will resist combustion and escape into the oil pan.
But fuel is not the only source of water contained in a generator. Water is the primary ingredient in the cooling system that prevents the friction caused by the moving parts from overheating. If minute cracks or fissures exist inside the combustion chamber, coolant will be prevalent in the oil pan reservoir.
On an operational generator the oil is scheduled to be changed after 300 hours of service, the oil filter included. *Maintenance Tip* - pour the new oil into the new filter before installing it in the machine. This will ensure the filter doesn't run in a dry state before being engaged by the rest of the lubrication system.
A more immediate concern is if the colour of the oil is a light grey. This is a sure indicator that water in some form is entering the combustion chamber, either through the fuel system or as coolant. Have the oil tested to determine the source and initiate further corrective measures.
Diesel Generator lubrication processes are not restricted to the engine. Some machines employ a drive shaft mechanism connected to a fan to assist air circulation. Proper lubrication, in the form of grease, will keep those mechanisms operating efficiently. Check those components at the same time as the oil change.
In addition to engine coolant, the lubrication system is also sensitive to changing temperatures. Refer to the manual or one of our technicians to determine the ideal oil viscosity for your operating conditions.
In our next installment we’ll burrow into the operating temperature of the engine: Hello Coolant!
Trinity Power is pleased to announce that we have partnered with R. STAHL, the world’s foremost innovator in explosion proof and explosion protected components and systems, to represent their TEMPEX explosion proof temporary power system in Weste...
Spring has arrived and, with it, unpredictable weather and the power outages that often follow. As recently as April 7th, a snow and wind storm caused a major outage in Ontario that affected 45,000 residents. Meanwhile, the spring melt in BC is see...
What does it take to deliver a bid-winning temporary power solution? In the case of our recent project at a phase III gas plant, the answer is: 2 designs, 5 vendors including Trinity Power, and 8 equipment locations spread across North America. ...