Why is a maintenance process so important?
Process is like a patient’s annual physical exam. The right process, like that annual exam, can be crucial in preventing a generator set from ever getting sick.
Following an established process can help protect a genset from otherwise inconsistent human behavior. As experienced as we might be, we are not always consistent in applying that experience in the field. Having a sound maintenance process is the best way to eliminate problems before they happen, and it can aid in the diagnosis of a small problem before it becomes a much larger one. Machines that can supply up to 2 megawatts of power require this kind of consistent service, especially when hundreds – or even thousands - of workers might be dependent on their output. So, what goes into that process?
The Log Book should contain detailed information regarding what regular maintenance procedures have been performed, when and by whom. A Log Book is neither a punch card nor a means of personnel evaluation. Instead, like a doctor’s chart, it’s a repository of data maintained throughout the course of a genset’s life and function.
And, like a chart, the Log Book should also be particular to the machine. Size and application have much to say about the nature of maintenance. Load size and fluctuation can greatly influence generator performance, along with a range of application-specific details, including: geography, latitude, altitude weather and temperature. All of these factors play important roles in the type and frequency of maintenance practices. Including this very critical information will aid the team of technicians whose job it is to ensure the smooth performance of the machine.
This information should be included along with the physical maintenance procedures performed on a regular basis. What regular maintenance procedures? Below is a guide, in chart form, detailing the most typical diesel maintenance schedule:
|Maintenance Items||Daily||Weekly||Monthly||Every 6 Months||Yearly||Exceptional Circumstances* (Cold Weather,Altitude,Etc.)|
|Inspect Charge-Air Piping||X|
|Inspect Engine Oil||X|
|Inspect Coolant Level||X|
|Inspect Fuel Level||X||X|
|Inspect Coolant Heater||X|
|Deplete Fuel Filter||X||X|
|Test Battery Voltage and Charge Level||X|
|Inspect Air Cleaner||X||X|
|Deplete Water from Fuel Tank||X||X|
|Inspect Coolant for Anti-Freeze Concentration||X||X|
|Inspect Drive Belt Tension||X||X|
|Deplete Exhaust Condensate||X||X|
|Replace Fuel Filters||X|
|Coolant Filter - Replace||X|
|Clean Crankcase Breather||X|
|Air Cleaner Element– Replace||X|
|Inspect Radiator Hoses||X||X|
|Replace Oil and Filter||X||X|
|Cooling System – Drain and Clean||X|
|* Exceptional circumstances indicate certain tasks may be performed more frequently than indicated.|
This is a general list. It doesn’t address all of the scenarios and situations in which a genset might be in service. Every machine and application is different but the process, once established, should remain consistent.
In subsequent articles we’ll provide further details into some of the more crucial elements related to generator maintenance. In that first item we’ll explore what to look for on your visual inspection: The Initial Patient Assessment.
Call Toll Free 1-888-758-4646 to speak with a power specialist about the next step in becoming emergency prepared.
Submit this form and a Trinity Power specialist will arrange an appointment to discuss further.
Trinity Power is pleased to announce that we have partnered with R. STAHL, the world’s foremost innovator in explosion proof and explosion protected components and systems, to represent their TEMPEX explosion proof temporary power system in Weste...
Spring has arrived and, with it, unpredictable weather and the power outages that often follow. As recently as April 7th, a snow and wind storm caused a major outage in Ontario that affected 45,000 residents. Meanwhile, the spring melt in BC is see...
What does it take to deliver a bid-winning temporary power solution? In the case of our recent project at a phase III gas plant, the answer is: 2 designs, 5 vendors including Trinity Power, and 8 equipment locations spread across North America. ...